Case study: Denmark’s largest wastewater treatment company uses BioSec®
After BIOFOS ran three independent field trials at their municipal wastewater plant in Avedøre, they chose to use BioSec® on an ongoing basis.
Denmark’s largest wastewater treatment company
Clean 104 million m3 wastewater/year
Serve 1.2 million people
Run three treatment plants in Denmark
Incinerate 24,000+ tons sludge dry solids per year
Generate electricity, biogas and district heating
Field trials lead to ongoing BioSec® use
The results of BIOFOS’ three independent field trials of BioSec® in 2017 and 2018 were convincing:
Cake dryness after mechanical dewatering increased by 1.5-1.6 %-points
Polymer consumption reduced by up to 15% (9.4 kg/t TS to 8.3 kg/t TS)
Reject water quality improved (lower TSS, COD)
So convincing, in fact, that BIOFOS has continuously been using BioSec® since April 2019. And nearly a year later, the Danish wastewater leader reported these results:
Up to 2 %-point improvement of cake dryness after dewatering
15% reduction in polymer consumption
Centrifuges running at lower speed (energy audit in progress)
"We have never seen such clean reject water before"
A plug-and-play solution
In the trials, BIOFOS doses BioSec® into the sludge stream between the anaerobic digester and the post-digestion sludge holding tanks. They allowed 8-24 hours of enzyme reaction time with the digestate before dewatering.
"Implementation and dosing start-up was both quick and easy"
One dose of BioSec® was tested in all three trials (0.25 kg BioSec®P and 0.25 kg BioSec®C/t TS; total dosage 0.5 kg/t TS).
Conditions during the field trials
BIOFOS evaluated the impact on dewatering of digested sludge by centrifuge based on:
Cake dryness after mechanical dewatering
Quality of reject water
They monitored the following operating parameters during both test and reference periods:
Digested sludge flow to centrifuges
Total solids flow to centrifuges
Ratio of primary and secondary sludge fed to digestion
Centrifuge settings were constant throughout. BIOFOS also monitored parameters known to influence sludge dewatering performance and took them into consideration during data evaluation. These include load of primary and secondary sludges to anaerobic digestion, anaerobic digestion performance, sludge load and flow to the centrifuge.